Elitech ECS-180B Temperature Controller With Cooling, Fan, Defrosting and Lighting/Alarm Four-way Control Outputs, With Evaporator Defrost Sensor, Condenser Sensor and Door Switch Input
2 sold in last 8 hours
customers are viewing this product
// Unavailable in the EU *
ECS-180B temperature controller could be used in the middle and low-temperature medicine cabinet, kitchen cabinet, supermarket split cabinet, air curtain cabinet, island counter, wine cabinet, etc.
Four-way sensor input: temperature probe sensor, condenser probe sensor, evaporator probe sensor, door switch.
Four-way control output: refrigeration, defrosting, fan, lighting/alarm relay.
|Cooling||Defrosting||Fan||Lighting / Alarming|
|Temperature Sensor||Condenser Sensor||Evaporator Defrost Sensor||Door Switch|
|Operating Voltage||220VAC±10%; 50/60Hz|
|Overall Power Consumption||<3W|
|Temperature Measurement Range||-50℃-90℃ (-58℉-194℉)|
|Temperature Control Range||-50℃-85℃ (-58℉-185℉)|
|Temperature Measurement Accuracy||±1℃(-40℃～50℃ ), ±2℃(51℃～70℃)|
|Mounting Dimension||71×29 (mm)|
|Input Sensor||Temperature Sensor, Evaporator Sensor, Condenser Sensor, Door Switch|
|Rated Current of Output Relay||5A/250VAC (Cooling, Lighting/Alarm)|
|Rated Current of Output Relay||10A/250VAC (Defrosting, Fan)|
|Front Panel Waterproof Level||IP65|
- The large panel of color digital tube, work status symbol display, the temperature display resolution is 0.1, the front panel waterproof level lP65.
- lt has a temperature sensor self-test function, and once test the failures, it has multiple protection and alarm methods. lt has the function of one-key recovery, and the rear adopts the plug-in connection method to effectively simplify processing for equipment manufacturers.
- The temperature measuring unit could switch between Celsius and Fahrenheit.
- With the function of Synchronous defrost switch signal detection, and it could form the network of real-time clock Synchronous defrost.
- Cabinet temperature over-limit alarm has two modes: absolute value and relative value.
- Light/external alarm relay could be selected by the software, and then select the function of external alarm relay, it could connect the remote alarm bell.
- If selected to install a standby power supply access unit, which could realize the function of off-power detection and alarm.
- With the complete control logic of hot-gas defrost start without the pressure difference in the refrigerant pipe, to prevent starting with the pressure, for the purpose of a longer compressor life.